The outdoor unit shall supply power to indoor unit via 14 AWG X 3 power wire High-voltage terminal block temperature sensor to disable unit in the event of power connection overheating
Auto-restart after power loss
Soft-start compressor minimizing current inrush
Base pan heater equipped as standard
All heat exchangers shall be mechanically bonded aluminum fin to copper tube.
The condensing unit heat exchanger salt spray test method: ISO-9227- The heat exchanger showed no unusual rust or corrosion development to 3,000 hours Integral condensate pump with maximum 29" lift from bottom of the unit with check valve and float switch to disable unit in the event of condensate overflow.
No Records Found
Contact email address is missing from your account. Please enter your email address and click update.